Product Specifications. • 9th edition approved UL • Capacity of up to 64 panels with zones of programming through software. • Powerful and versatile . FireNET FN/FN UL/FM approved. Expandable loop and connect to other panel. ANALOG ADDRESS FIRE CONTL PAN, Hochiki. Description: Analog Address Fire Contl Panel; Category: Addressable Panels, Fire Control Panels, Fire; UPC.
|Published (Last):||1 April 2012|
|PDF File Size:||17.9 Mb|
|ePub File Size:||14.81 Mb|
|Price:||Free* [*Free Regsitration Required]|
Dome Camera p Turbo HD, 2. These are hovhiki separate box with a power supply, battery charger, batteries, and NACs. Home Shop Store Contact us.
Post Mon Feb 27, 6: For manual call point placement inside SLC loop what control module is used? One NAC at 1.
Addressable System (Multiplex)
Any power consumed by devices connected to a SOM powered by the panel is also part of that 4 amps. I have some more basic hochjki.
Can you give me a diagram of your suggestion? User Control Panel Profile Logout. I don’t have any practical experience. While studying the installation manual of firenet analog addressable system there are something confused me.
CNL PANEL 2LOOP 4AMP PS CHARCL
These outputs may be used for a variety of purposes including door holders, elevator recall, and other fire safety functions. The communicator may be configured to report by zone or by address point. That means when detectors detects then all horns will sound automatically but not supervised.
With 4 amp current we can only connect a few horn strobe. Thanks for your reply. Yes, this would be the SOM. But what i posted will it work or not? Fn2-127 means 4 NACs at 1 amp each. NAC only can supply 4 amp only. Keep in mind the power available for NACs is limited. Sorry but I cannot give an exact answer to such a generic question.
Only to supervise notification devices?
Hochiki FN-DAC | COMMUNICATORS
Which devices should connect with this module? Then there should be a module to control Sprinklers system and a signal should be sent to that module from a control panel to activate the Sprinklers.
The SOM provides a supervised 24VDC polarity reversing output on the SLC loop most commonly used for audible and visual signaling appliances or triggering a remote notification appliance circuit power expander. I know this is illegal.
FN/FN FireNET Control Panel
In other words, there is no hard set limit. I am just stared learning the system.
I don’t know i am right or wrong. That is not legal and could put you and your employer in jeopardy. In the control panel there is 4 NAC connection points.
Post Thu Mar 02, 1: All Rights Reserved To use a standard contact type call point there is a selection of modules uochiki in the manual. Post Sun Mar 05, 6: Will this connection work? Can you please explain hpchiki we use SOM? I know that if I use som module then I can conncet many horn within a panel. If i use a automatic Sprinklers system then the basic is if there is a fire then detectors detects and send a signal to control panel that there is a fire, then control panel send a signal to notification devices to alarm.
Post Mon Feb 27, 5: Up to devices can be placed on a single SLC loop.